Amp & 350,000 Amp Surge Capacity for Single & Three Phase
panel-mount Surge Protectors, the 230,000 Amp pictured below and
the 350,000 Amp pictured at right, are hard-wired directly to Service
Entrance and Distribution Panels and are available for Single Phase
120/240 VAC and Three Phase, 3 and 4 wire models up to 277/480 VAC
Systems. Ideal for preventing the gradual deteriorating effects
of brownouts and
raw power to electrical equipment, as well as the hazards of catastrophic
failures from surges, sags, spikes, glitches and lightning that
wreak havoc with your electrical equipment, computers and internal
appliances. Easy to install, our surge protectors are warranted
for five full years.
from internal and external spikes and surges
grade waterproof & vapor tight enclosure
test to verify on-line protection
Load Current (Nominal per phase)
Type Cooling with Heat Sink Encapsulants
Amp model covers 120/208V WYE, 120/240 WYE or Delta or 277/480V
WYE or Delta for 3 Phase systems
is less than 5 Nanoseconds Nominal
99+% Full Load
3% to 94% Non-condensing
Code Per NEMA Standard
housing 4.5" high, 4.65" wide, 3.25" deep
have installation performed by a bonded, licensed electrician.
Wye or Delta
Operating Voltage (VRMS)
of Leads (#12AWG)
Surge Current Per Phase
Surge Current Capacity
Constant Voltage (L-N/L-L)
Fuse Link ** Protected
Full Replacement Warranty
Category B, 8x20 milliseconds - 500 AMPS
**Safety FuseLink up to Maximum Rating
(A) CEM#06328 can be used for 3 or 4 wire systems by removing the
WHITE Neutral Wire during installation.
(B) Add 1" Height for optional 'SWIVEL STAND-OFF' mounting
through 3/4" knockout.
(C) Lifetime 'REPLACEMENT PROTECTION MODULE' Warranty Fee @ $100
for either model in series.
(D) Internally Fuse-Linked to maintain fully rated surge capacity
with safety during catastrophic failures.
Verify voltages on each wire in Power Panel with a voltmeter
2) Turn off Main Circuit Breaker
3) Locate and remove desired 3/4-inch knockout in Power Panel
4) Mount Transient Voltage Protector with included Chase Nipple
5) Connect WHITE wire to NEUTRAL BUSS, GREEN WIRE to GROUND BUSS.
Connect the BLACK or RED WIRES to a circuit breaker on the left
side. Connect the other BLACK or RED wire to a circuit breaker on
the right side as shown in the illustration at the right. DO NOT
CONNECT THESE WIRES TO THE MAIN CIRCUIT BREAKER!!
6) Turn on the Main Circuit Breaker
is a typical installation for the Transient Voltage Surge Protector.
If you have further questions contact